A User ID is a user name and password that can be used to access several Honeywell Web sites.
You must first provide some basic account information. All fields marked with an asterisk * or "Thumbs down/up" symbol are required and include an easily-remembered User ID, Password, First name, Last name, and Email address. To help protect your account, you must also provide three Security Questions and Answers. You provide the Password, Email address, and each Security Answer twice to help avoid accidental typos.
Combined acoustic and optical alarm signaling device is EN 54-3 & EN 54-23 compliant, in red housing, and offers a selection of 32 signal tones including the DIN tone and other country-specific tones. All tones comply with EN 54-3. Tone configuration takes place via a 6-pin DIP switch. Up to two different signal tones may be activated. The optical signaling device with red signal lamp is suitable in accordance with EN 54-23 for square signal ranges W-2.4-6.0 and cylindrical signal ranges C-3-8.9 / C-6-8.2. Signaling device with flat base, suitable for wall and ceiling mounting. To help define your conventional Visual Alarm Devices (VADs) requirements in line with the EN54-23 standard, we have developed an easy to use online guide. Simply enter the room dimensions and ambient light conditions and the guide will help your device selection: http://www.kac.co.uk/EN54-device-chooser.htm